Fault Code A7: Malfunction of swing flap motor.
Fault: Malfunction of swing flap motor
Defective swing flap motor
Defective indoor unit PCB
Defective connection cable
Defective airflow direction adjusting flap-cam
For Daikin split and multi-split air conditioning systems included wall-mounted, duct-connected, floor-standing, multi-flow, stylish, european, ururu sarara & cassette-type units.
If molded case circuit breakers or earth leakage circuit breakers have tripped, do not reset the breaker immediately without first checking for any problems with insulation of equipment.
Resetting breakers without a check of insulation may cause damage to equipment.