Brivis Error Code 65 Motor Lockout: While the fan limp fault is registered and a motor open circuit occurs or an overheat cool down is initiated the motor lockout fault is flagged.
For Heater Repair Tech Only
Reason: The unit is locked out due to fan motor open circuit (Error 60), and the fan motor speed sensor signal has not been received by the NG-2 (Error 30). OR The unit was operating in FAN_LIMP mode (Error 30), and an over temperature condition has occurred (Error 40, 41, or 42). Service Check List: Refer to Check Lists for Error Code 30, 40, 41, 42 or 60, whichever has occurred.